- Click Get Serial Number or Get Calibration Date buttons. For a visual example, see Figure 31.
You can set the alternate secondary address of the module as well. The unit responds to both the DIP switch set address and the software set alternate address. The DIP address can be used for initial setup and small clusters of UVMs. If more than 16 units are on the bus, use the alternate software address.
- Set the address of the UVM module that you want to interact with from
addresses 0 to 15. The addresses are from the DIP switches on the unit. See Table 9 for more
information.Note: The unit can have an internal secondary address, labeled +16, that it responds to automatically.
- To confirm that communication is present, click Get Revision. The revision number appears in the Misc tab module revision box.
- To save a copy of these settings to your computer, click Save Displayed Values to File.