The required points must be mapped under the TDA Module. To map the points, select the TDA Module device under the BACnet Integration and choose Field Point from the Insert menu. If necessary, refresh the tree view to see a newly added TDA Module. Refer to Table 2 for a list of supported points on the TDA Module.
When mapping points offline, the point type must match the BACnet object type (for example, AI, AV, MV, or BO) and the point instance number must match the BACnet instance number.