The Operator Menu has the sub-menu selections shown in the following table.
|Enables the configuration of system variables such as: fan area, elevation, relative humidity, flow units, and zero cutoff.
|Enables the selection of display parameters on LCD lines and display filtering.
|Output 1 Parameters
|Enables the selection of Analog Output #1 Parameters: temperature, flow, or none for Analog Output #1.
|Output 2 Parameters
|Enables the selection of Analog Output #2 Parameters: temperature, flow, or none for Analog Output #2.
|Temperature Low Pass Filter
|Temperature low pass filter
|Flow Low Pass Filter
|Selects amount of filtering applied to the Analog Output for flow.
|Analog Output Calibration
|Sets the zero and span of the analog outputs for temperature and flow.
|Temperature Balance Menu
|Enables the selection of an offset to be applied to the reported average temperature of a selected fan.
|Menu Inactivity Timeout
|Enables the selection of a time after which the unit returns to normal operation display mode and turns off the front panel back light, if there is no detected activity from the keypad.
|Turns the BACnet ON or OFF and enables configuration.
|BACnet Flow Alarm Configuration
|Enables selection of the flow object of the selected fan to turn high and low alarms ON or OFF, high and low setpoints, dead band, and alarm delay.
|BACnet Temp Alarm Configuration
|Enables selection of the temp object of the selected fan to turn high and low alarms ON or OFF, high and low setpoints, dead band, and alarm delay.
|Enable Operator PIN
|Enables the selection of a PIN to access the Operator Menu.
|Change Operator PIN
|Change the PIN to access the Operator Menu.
|Operator Menu Exit
|Returns the display to normal operation.