- One of the following:
Note: A dedicated transformer is required (it cannot power additional equipment).
- UL listed, Class 2, 24 VAC transformer, rated at minimum of 20 VA
- 24 VDC power supply, capable of supplying at least 1A (24W)
- FX-SC8XPS-0 wall-mount AC power adapter with barrel connector plug
- DIN rail, type NS35/7.5 (35mm x 7.5mm) and DIN rail end-clips (stop clips), recommended for any installation that includes option modules.
- Suitable tools and fasteners for mounting the unit and any accessories.